Question about Electrical Supplies
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
You could use 6/3 with ground. You must take an equipment ground conductor along with your current carrying conductors. Still drive a ground rod at the building, and add a seperate ground bar in the sub panel. Connect your equipment grounding conductor from main building along with the equipment grouding conductor to the ground rod. Do not bond the neutral in the sub panel to ground. Be aware you will still have some voltage drop, so a 220V air conditioner might be better.
Posted on Sep 24, 2010
Tips for a great answer:
Jun 22, 2017 | The Computers & Internet
Dec 23, 2014 | Games
Aug 15, 2012 | Square D Qo 100 Amp Breaker Box Qo120m100...
Aug 15, 2012 | Your One Source Homeline Load Center, 200...
May 11, 2011 | Orange Cell Phones
Feb 25, 2010 | Schumacher 1000 Watt Inverter with 2 GA....
Jul 06, 2009 | Sub-Zero 632 / S
Apr 14, 2009 | Sony Xplod XM-1652Z Car Audio Amplifier
Nov 17, 2008 | Creek Audio Players & Recorders
329 people viewed this question
Usually answered in minutes!