Question about Carrier Heating & Cooling
If unit displays "e4"
1? Check whether the winding resistance and
operation current of the compressor are normal.
2?Check whether the high and low pressure is normal
when the unit is running.
3?Check (whether the coil pipe sensor is normal)
whether the contact of the inserter on the circuit
board is well, the coil pipe temperature sensor is
fixed, the evaporation of the indoor unit is well,
the key is to check the evaporator temperature
detected by the coil pipe temperature sensor has
reached the cooling or heating temperature.
4?Check whether the surface of the condenser is too
dirty, it should be cleaned when it is too dirty.
5?Check whether the capacitance of the outdoor motor
and the fan is damaged, it should be replaced when
it is damaged.
6?If the above items are normal, the electric control
board should be replaced.
Air Condition Fort lauderdale
Posted on Apr 12, 2015
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get 2 Free calls (no credit card required) and instant help on almost anything you can think of (from cars to computers, appliances, handyman, and even pets).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 27, 2016 | Carrier Heating & Cooling
May 10, 2015 | Carrier Heating & Cooling
Apr 07, 2015 | Heating & Cooling
Sep 26, 2011 | Heating & Cooling
Jan 15, 2011 | Soleus MA-9000AH Air Conditioner
Jun 10, 2009 | GE APH10AA Air Conditioner
May 01, 2009 | Carrier 36KCARMS Air Conditioner
May 07, 2008 | Carrier XHC101D Air Conditioner
123 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: