Question about Heating & Cooling
Is gas on?
Is it a Good spark?
Sparking where it should and is it subdued at all?
If good strong spark, the there should be ignition, either No fuel, or Pilot valve of gas valve not opening. If you can confirm proper voltage to pilot valve, then you can ascertain if it's a bad gas valve or ignition module.
Posted on Apr 12, 2015
Move the spark source close to the pilot flame area by bending or another method of adjustment.
Posted on Apr 12, 2015
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Make sure all the wire connections are good and tight. Next lift off the cover and look for a little thermal disc mounted up by top of the heat exchanger. Most have a re-set button but not all. If you have this ,by-pass it ,see if that solves the problem, if so it may be defective, or doing its job and you have a venting problem. If you don't have this and have changed the thermocouple (was it a copper tube with a fitting that screwed into the gas valve, or did it have 2 wires, that is a pilot generator, kind of same thing) make sure the probe is set correct, with the pilot flame heating the top 1/3rd of the probe. The only thing left is the gas valve.
Posted on Dec 25, 2007
SOURCE: Williams wall furnace, top vent.
I've replaced a Williams wall gas heater non-electric. The thermostat is connected right and mounted on the wall. But, there's a thick black copper wire on the side of the furnace tagged thermostat. I don't know what to do with it? Where do you connect this wire? When it touches the top screw of the three screws running vertically(where the other wires are connected). The burner lights up and stays on, even if you play with the wall thermostat. Touching the other two screws doesn't do anything. Now, the manual talks about connecting it to the venting wires? Extra wires coming from the top or maybe somewhere else in the wall? I've left it connected to the first screw, ran the heater. But, it never turns off? Any suggestions? Thanks
Posted on Feb 23, 2008
Make sure you have gas to the unit and the switch on top of valve is turn to on. Can you here the gas valve click? It igniter comes on and a delay and the gas valve should come on. Kill power to furnace to reset control board. Rus Let me know how it goes.
Posted on Nov 17, 2009
On a call for heat, the 24 volt thermostat sends a signal to the control module. The control module will indicate a call for heat with a light on the control either blinking or remain solid depending upon model. The inducer (exhaust) blower will purge all gasses from the furnace and pressurize a pressure switch. Once the pressure switch tells the module to continue, the electronic ignition will energize and send 120 volts to the igniter. The igniter will glow and you will be able to see it if viewed thru the small inspection port. Once the igniter gets hot enough, it sends a signal to the module opening up the gas valve (24 volts). Either a pilot will come on or the burner tube will ignite then spread the flame to all burners. Lastly a safety sensor will be looking for a certain temperature within a few seconds and the furnace will continue to operate and the room air blower will turn on in a minute or two.
What could go wrong? The unit will not run if there is no signal from the thermostat (bad thermostat or broken wire), the control module does not sense a signal from the thermostat (bad control), the inducer does not energize (bad motor), the pressure switch does not close (blocked vent piping, bad switch, plugged condensate hose), the igniter does not energize (bad control, bad igniter), the gas valve does not open or there is no gas (bad gas valve, broken wire, no gas), the pilot does not light (dirty pilot), the burner does not light (bad burner, plugged orifice, not enough combustion air), the flame does not spread to each burner (bad flame spreader, dirty flame spreader, more bad burners), the flame safety sensor does not detect flame (dirty or bad flame spreader, bad flame sensor, broken wire, bad control), or the room air blower does not energize (bad fan motor, bad control).
Your furnace has a diagnostic chart on the reverse of the lower panel incorporated in the wiring diagram. One blink tells you that it is a failure but wont tell you where to start looking.
Posted on Nov 28, 2009
Tie red and white wires together after removing thermostat from wall, if unit comes on replace thermostat, if not check limit controls for continuity, Good luck.
Posted on Mar 07, 2010
Tips for a great answer:
Apr 12, 2015 | Heating & Cooling
on Mar 20, 2010 | Heating & Cooling
Feb 27, 2015 | Heating & Cooling
Feb 05, 2011 | Heating & Cooling
Feb 26, 2010 | Heating & Cooling
Sep 07, 2009 | Kenmore 30169 Electric Single Oven
Jan 01, 2009 | Heating & Cooling
Oct 17, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
60 people viewed this question
Usually answered in minutes!