Question about Heating & Cooling
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Check each screw on your compressor to ground (compressor case). Should be very high resistance Then check the resistance across your teminals on the compressor to be sure it is not shorted. Then check the wiring to your capacitor (The big one). I ran across this just last week. The mechanic didnt have the capicator wired correctly. If it is brand new it will have a wiring schematic somewhere on it.
Dont leave the compressor on very long, but turn it on long enough to get a voltage reading across the terminals. I assume it should be 240 volts. If you have check all of this, they make a jump start gadget to start a stuck compressor. They sell it just about everywhere. Let me know how this comes out..
Posted on Sep 30, 2008
Easiest thing to do is pull the motor out and take it to Grainger. They can probably match it with a Dayton brand. No HVAC place will sell you a motor. They are all wholesale, and not to the public. You really don't have a whole lot of options here.
Posted on Feb 21, 2009
Yes it could be the pop off pressure relief on the compressor.
I assume it is the outdoor fan your referring to not running.
If this is a heat pump and it is in defrost (only in the heating mode should your outdoor fan be off and then for only a max of 12 to 15 minutes).
If it is just AC ir is Heat pump in cool mode, the out door fan should run while the compressor and indoor fan are on. Until the thermostat is satisfied on room temp.
This high pitched squealing is indicative of a bad fan motor or capacitor for the out door fan motor. Kill power and test blades to see if turns free. Check the run capacitor inside control panel. It is usually silver or aluminum colored (some are painted gray). The top should be flat with rolled edges and the sides should either be round or oval shaped with no swelling or oil leaking from inside it. If this all looks normal take it to where your going to get a motor any way and ask them to check it or sell you a replacement at the same time. These can go out usually from high voltage (lighting...) or from over heating (bad fan motor, dirty out door coil...).
Hope this helps you if not post back I'll respond as soon as I can. And please rate me as high as you can. Thank you for using Fix ya and good luck.
Posted on Mar 28, 2009
Tips for a great answer:
Apr 11, 2016 | LG Window Ac Unit 18000 Btu, Energy Star...
May 25, 2014 | Haier 18000 Btu Air Conditioner Heat Pump...
Sep 11, 2013 | Mitsubishi Mr. Slim MXZ30TN Air...
May 30, 2012 | General Electric Heating & Cooling
Dec 15, 2010 | Panasonic CW-XC143EU Air Conditioner
Nov 30, 2010 | Ruud UBHC Air Conditioner
Jul 01, 2010 | Maytag M6Y18F7A Air Conditioner
May 15, 2009 | Goodman CKL60AR60 Air Conditioner
37 people viewed this question
Usually answered in minutes!