Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: fan motor of my Panasonic
Do you know a service tech? Wholesale houses have generic motors for these now at about 1/3 less then normal price. Warning be prepaired to pay a higher then normal price due to the copper shortage...
Posted on Apr 26, 2008
SOURCE: Fan not running on outdoor unit
yes it could be the capacitor open or shorted possiblity.
check the motor to be sure it turns free?(disconnect power first)
check with a voltage meter the wires coming from the fan motor to its power source and see if there is the required voltage there for it to operate?
Feel the motor is it hot? or not hot?
If it is hot then you could have a shorted capacitor causing the motor to overheat
check for a burning smell also.
Take an ohm reading across the motor wires after you turn the power off and disconnect the motor wires.
pick your two power wires from the motor and ohm them do you get a reading? the motor is good
no reading motor is bad or overheated and out on internal overload..
Posted on Jun 15, 2009
the fan motor is burt. replace it. it will still spin if you manually engage but it will overheat an may even cause fire, also that waste tremendous amount of electricity now.cap is not defective,
Posted on Jul 04, 2009
Bearing in fan going out. Let it run till it quits or call service tech to change motor. Fix cost about 250 to 300 dollars. russ
Posted on Jul 22, 2009
Tips for a great answer:
Sep 19, 2016 | Heating & Cooling
Jun 07, 2016 | Heating & Cooling
Feb 22, 2015 | Inverter Heating & Cooling
Aug 22, 2014 | Honeywell Electronic Programmable...
Jan 12, 2012 | Panasonic Heating & Cooling
May 31, 2010 | Fujitsu 24R1 Air Conditioner
Apr 18, 2010 | Heating & Cooling
Jan 16, 2010 | Panasonic Heating & Cooling
Jul 22, 2009 | Carrier Heating & Cooling
May 31, 2009 | Heating & Cooling
29 people viewed this question
Usually answered in minutes!