Question about Goodman Heating & Cooling
If what MM suggested doesn't work, I would say that the refrigeration system isn't working. Pre def means that the indoor unit is waiting to get hot before it starts again. Feel the coil behind the filter, it should be getting hot when on heating mode. If its getting hot and the machine is still sitting on pre / def, it is most likely that the indoor pipe sensor has failed. This sensor triggers the indoor unit to start once it has reached operating temperature. If the coil is not hot, check that the outdoor unit is actually running. When on heat mode, the outside unit should be blowing cold air as the hot refrigerant is now going inside. If the outside unit is blowing warm air , then that would indicate that the reversing valve system is not operating.
Posted on Apr 13, 2015
You have to try resetting the system. First turn the breaker off for the condenser and wait about 20 seconds. After you turn it back on the system should reset.
Air Conditioning Repair Tamarac
Posted on Apr 12, 2015
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 24, 2016 | Toshiba Computers & Internet
Dec 09, 2014 | Heating & Cooling
Oct 06, 2012 | Goodman Manufacturing GMH950453BX - 45,000...
Dec 11, 2010 | Goodman GMS90703BXA Heater
Jan 12, 2010 | Goodman GMS80453ANA Open Flame Mid-Size...
Jun 12, 2009 | Heating & Cooling
Jun 18, 2008 | Heating & Cooling
717 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: