Question about Honeywell HE440A1005 Humidifier
We just moved into a 7 year old home that has the above. This morning discovered the over flow drain was pouring quite a stream of water. Turn off power and water. How should I fix?
Honeywell has had lots of problems with this humidifier. They are coming out with a completely redesigned steam humidifier that will be available in a month or two. If you know who installed it (through equipment stickers and such) you can probably get them to swap your old trouble prone unit for the new design for just the labor. If they won't, then push them to talk with their Honeywell distributor about it.
The problem is most likely a stuck float in the humidifier. There are two floats that run up and down. One that tells it when to add water, and one that is a safety. They both tend to get stuck with mineral deposits.
You can fix it by unplugging the humidifier, turning off the water, draining the pan (unscrew the drain on the bottom a few turns), disconnecting the water lines and wires (2 molded plugs and 2 screw terminals-don't worry about if they get swapped). There should be a couple of screws that lock it into the ductwork such that when you remove the screws you can pull the whole unit out to see inside the water tank. Then just clean everything out well and put it back together in the same order.
You really do want Honeywell to get you a new humidifier though.
Posted on Nov 17, 2007
One of the problems in this He440A is the the Relay Honneywell part no. 320064445-001 (4 total) . The terminals (5 total) and especially the two smaller 24 volt coil terminals are a big problem. The wires for the 24 volt coil are soldered directly to these terminals, and the complete relay is shoved in the case. So if you are testing the relay and happen to pull the wire lugs off the terminals, and most don't come off without some pulling and wiggling of the lug, then there is a good chance you will pull or break the coil wire attached to that terminal. Well then, what is the solution????? The problem has been corrected. The relay manufacturer now puts epoxy around each of the 5 terminals were it exits the case. Now the teminals can move when you remove a terminal lug.
Posted on Dec 18, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 10, 2015 | Humidifiers
Nov 14, 2007 | Honeywell HE440A1005 Humidifier
Jan 26, 2015 | Honeywell HE120 Humidifier
Feb 21, 2011 | Honeywell Power Humidifier: Furnace...
Nov 30, 2009 | Honeywell HE440A1005 Humidifier
Nov 21, 2009 | Honeywell Power Humidifier: Furnace...
Dec 20, 2008 | Honeywell Power Humidifier: Furnace...
Dec 18, 2008 | Aprilaire 600 Humidifier
Jul 02, 2008 | Honeywell Power Humidifier: Furnace...
Oct 27, 2006 | Honeywell HE360A1027 Whole House...
Aug 31, 2017 | Honeywell HE440A1005 Humidifier
Dec 23, 2008 | Honeywell HE440A1005 Humidifier
762 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: