Question about LG LMN096HVT WaMounted Mini Split Indoor Unit - 9000 BTU
Posted by Anonymous on
Try resetting the system. First turn the breaker off for the condenser and wait about 20 seconds. After you turn it back on the system should reset. If you have any other Air Conditioning Repair Questions don't be afraid to let us know
Posted on Jul 08, 2016
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
You should also check the outside unit to make sure the coil is not clogged with dirt or grass clippings and the fan is working. The reversing valve that switches it from cool to heat could also be a problem. If it isn't shifting it will not switch between heat and cool.
Posted on Apr 29, 2010
You have a control board issue. You can get a new control board by Google searching the make and the model of the unit. There are several sites that sell them
Posted on May 24, 2010
Indoor Pipe Sensor or Outdoor Sensor Assy fault, Open or Short. Disconnect from PCB and measure resistance. Air sensor = 10 kOhm at 25C, Pipe sensor = 5
kOhm at 25C. If not replace sensor. Thanks.
Posted on Feb 05, 2011
Tips for a great answer:
May 21, 2017 | Honeywell Heating & Cooling
Oct 17, 2015 | Thermostats White Rodgers 1F80-261...
Apr 07, 2015 | Seat Cars & Trucks
Jul 28, 2014 | Samsung AQV12VBE Vivace Wall Heat Pump Air...
May 19, 2017 | Heating & Cooling
Jan 05, 2011 | Computers & Internet
Mar 24, 2010 | Honeywell Electronic Programmable...
Sep 20, 2009 | Heating & Cooling
Aug 10, 2009 | American Standard Heating & Cooling
Apr 05, 2009 | Heating & Cooling
62 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: