Question about Heating & Cooling
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: oil trap for 2 ton split unit
Pipe size is okay, not that I know any better than the manufacturer, but I would recommend at least two and possibly even three oil traps in the vapor line on the way back up.
Posted on Jun 15, 2008
No. 75' of distance between condenser coil and evaporator coil is not considered abnormal at all. I would look elsewhere for reasons your unit does not cool in very hot weather, i.e., dirty condenser, low charge, improper sizing of AC and cooling space to name just a few.
Posted on Jun 11, 2011
Tips for a great answer:
Sep 02, 2013 | Heating & Cooling
Aug 26, 2013 | Goodman CKL36AR36 Air Conditioner
Aug 21, 2013 | Sunbeam Heating & Cooling
Jul 31, 2017 | Noritz N-069M-DV, N-084M, and N-084M-DV...
Jul 09, 2017 | Altec Lansing 221 Computer Speakers
Dec 11, 2010 | Heating & Cooling
Nov 29, 2010 | Heating & Cooling
Sep 03, 2010 | Goodman Heating & Cooling
Aug 19, 2010 | Goodman CKL60AR60 Air Conditioner
Oct 05, 2008 | Goodman CLQ36AR49 Air Conditioner
59 people viewed this question
Usually answered in minutes!