Question about LG Heating & Cooling
Capillary size and length in .75 split ac of lg
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
what you have left out is the thermostat and they relays(electrical) which are activated by the thermostat. Another point is the door closing button near the bottom right side mounted on the body of the fridge. Check it out too.................................sodeep
Posted on Jul 26, 2009
The best practice when replacing a cap tube is to replace it with the identical size and length of the old cap tube. Also, you must run it in the same way, if the cap tube was soldered to the suction line in any area then the replacement should also be soldered to the suction line. The old cap tube should have been stretched out, measured and gauged with a cap tube gauge. If you just went by load, it appears your cap tube is the wrong size, should be a #4 or .064ID and not a #5 .028ID. This is just based on some cap tube sizing charts I looked at assuming you have a single cap tube and not a multi circuit evap. Other than the cap tube the symptoms point to a system that was overcharged, dirty condenser, condenser fan motor not running. If you have a way to check suction and discharge pressures this will be the best way to see what is going on.
Posted on May 10, 2014
I'm guessing you should have 3/8 & 5/8 copper on that unit with a maximum of 50 feet. I doubt the line set size is affecting your pressures that significantly, you likely have a leak.
Posted on May 05, 2017
Tips for a great answer:
May 05, 2017 | Heating & Cooling
May 10, 2014 | Heating & Cooling
Aug 24, 2013 | KitchenAid Refrigerators
May 29, 2012 | Furniture
Apr 20, 2011 | VinoTemp VT200
Feb 27, 2011 | 1986 Oldsmobile Regency
Jan 10, 2010 | 2002 Nissan Xterra
Jun 11, 2009 | Dometic Rooftop RV Air Conditioner
Jun 09, 2008 | LG Heating & Cooling
Jan 04, 2008 | Sanyo 24KS62R Cool Mini Split Air...
26 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: