Question about Fujitsu Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: i have a Fujitsu ASTA24LCC
Check your filters. Manual says they need to be cleaned every two weeks under normal operation (and in my case more often during renovations). It seems it may not take much to limit air flow enough for the indoor unit to trip out. Hope this helps.
Posted on Aug 24, 2008
if no cold blowing,evaporator is not working,have you ever heard compressor is running,check this out,no compression of course you dont have cool on evaporator.if the compressor is running check the oprating current,if still have enough freon charge,if not running check thermostat reset setting on the coldest,ifn still not run check overload relay on panel control reset lever to put back compressor to run,check condensing fan if working,if not check also over load protection,this should be done by ac tech nician.have a nice day,dont gorget to rate me, thank's
Posted on Apr 18, 2009
I have same problem like yours to my newly installed Fujitsu multi-split system (the first time use since system installed 1 week ago). I rang the electrician who did the installation; he said it must be the units themselves nothing to do with electricity.
Okay, then I rang Fujitsu and their local service agent. They suggested me to switch off C/B for an hour to reset the units. I followed the instruction but the indoor units still did not respond to remote control...
It simply looks like no power supply to indoor units (they are hard-wired to the outdoor unit). So I used a multi-meter to test the power terminals of indoor units (Danger! If you have no idea about this, don't even try! ): it seemed no power supply even C/B is on. I turned to the isolator which next to the outdoor unit. The isolator was making arcing noise when I switched it on and off. The indoor units suddenly turned on for few minutes then died again.
So I figured out the problem is that crooked isolator. I called the unhappy electrician to replace the isolator. End story....
I hope my experience will help you a little bit.
Posted on Nov 23, 2010
Tips for a great answer:
Nov 15, 2016 | Fujitsu Heating & Cooling
Jul 11, 2015 | Heating & Cooling
Feb 10, 2015 | Fujitsu Heating & Cooling
Feb 01, 2014 | Fujitsu Heating & Cooling
Feb 02, 2011 | Heating & Cooling
Dec 11, 2010 | Fujitsu Heating & Cooling
Jul 11, 2010 | Fujitsu 24C1 Air Conditioner
Mar 01, 2010 | Fujitsu Heating & Cooling
Dec 13, 2008 | Fujitsu 18C1 Air Conditioner
672 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: