Question about Ruud Heating & Cooling
Air Handler used is a RUUD UEAB 1005BNS
If you are trying to reset the breaker and it trips as soon as you go to on, you have a dead short or a bad breaker. If you can hear the compressor, if it just hums or vibrates most likely it has an internal short and needs to be replaced.
Posted on Apr 07, 2015
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get 2 Free calls (no credit card required) and instant help on almost anything you can think of (from cars to computers, appliances, handyman, and even pets).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
I dont have axcess to a wiring diagram but i am pretty familiar i know the heater wiring is crazy on these what are you having trouble with??
Posted on Nov 24, 2007
Relay could be problem. See if thermostat makes relay click. If it does and you hear compressor try to run when it closes, everything is good in control circiut. Then check Start and Run capacitors. May be just one capacitor with 3 terminals on it. If there is any oil leaking out of it or if its swelled, Thats the problem, Replace it with same size capacitor. Mark wires before you remove them. If you hear relay try to close but no sound from the compressor, Check the High Pressure switch. They usually have a red reset button. If its tripped, Could be the condensor fan motor or grass and **** blocking air flow on condensor coil. If you hear no compressor noise and high pressure switch is not tripped but relay acts like its working, Replace relay. DANGER!!! High Voltage!!! Make sure that all power is off of both units before touching wires. Hope this helps. Let me know. Am on yahoo IM as kstfas if you yahoo.
Posted on Jul 05, 2008
SOURCE: Wiring Diagram
here is a basic wiring diagram for all air cond systems your thermostat consist of treminal r w y and c run a four conductor wire fromm thermostat to ai handler the air handler should allso have eather have red blue white wires or a teminal block marked r w c r stands for red w for white c for comon allso blue run color for color from the thermostat to ai handler with exeption of yellow yellow runs straigth to condenserand retuns in white wire to air handler wich gets conected to comon hope this help[s you
Posted on Jul 23, 2008
mfg date are coded into the ser.# useualy fist 4 digits are yr and month of MFG. 0306 would be 2003 june ect. if in doubt call amanna dealer and ask them. Steve
Posted on Jul 12, 2009
we are trying to install a goodman heat pump with a rheem air handler, the orange wire is hook up and the unit is still staying in the heat mood. does anyone have a wiring diagram for the air handler, their is some white wires in the air handler one with a purple strip and one with a black strip we need help
Posted on Aug 19, 2009
Tips for a great answer:
Sep 23, 2015 | Dryers
Sep 02, 2015 | Goodman Heating & Cooling
Apr 10, 2013 | Heating & Cooling
Jul 31, 2011 | Heating & Cooling
May 14, 2011 | Carrier Air Tools & Compressors
Jan 02, 2011 | Goodman CLJ30AR32 Air Conditioner
Oct 29, 2010 | Campbell Hausfeld Maxus 60 Gallon (Belt...
Sep 05, 2009 | Heating & Cooling
Jun 15, 2009 | Heating & Cooling
Jun 12, 2009 | Honeywell Programmable Thermostat Heater
53 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: