Question about Heating & Cooling
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: Pool Heater
You can light the pilot with a B.B.Q. lighter.
Nottoohandy. Backwash you filter, make sure it's really clean. If that doesn't work it could be the pressure switch. You can by-pass the switch with a piece of wire to see if it fires up. If it does, it's the switch. There is a picture of the switch in the manual.
Posted on May 26, 2008
The easiest way to troubleshoot any heater, is to call the manufacturer. Their techs will walk you through each possible problem and solution until you find the answer.
Posted on Oct 03, 2008
The thermocouple [s] require replacement, or in my experience try servicing the unit first. There is an injector for the main pilot and a secondary injector for the flame thrower ignition. Both of these are prone to blocking due to dust and can be enough to shut the unit down. Although usually this is thermocouple related as you are manually keeping the unit running when you hold down the button, if the tcouple is broken it wont send enough millivolts to hold the magnetic valve open when you release the button.
Posted on May 31, 2009
Tips for a great answer:
May 27, 2016 | Water Water Heaters
May 17, 2016 | Heating & Cooling
Mar 28, 2015 | Cars & Trucks
Jan 30, 2014 | Heating & Cooling
Feb 11, 2013 | Bradford White Bradford MI30T6FBN-337 30...
May 06, 2011 | Rinnai Vent-Free Gas Heater: Blower For...
Dec 12, 2017 | Water Heaters
Nov 07, 2009 | Heating & Cooling
Sep 21, 2009 | Heating & Cooling
42 people viewed this question
Usually answered in minutes!