Question about Mitsubishi Mr. Slim MXZ30TN Air Conditioner
I have a mr slim mitsubishi ceilling mounted unit but there is no heating come from the unit and sometimes a sign o P8 and E0 are displayed in the LCD please help Abi
P8 refers to outdoor protection device activation usually caused by low gas charge or blocked condenser coil. any good a/c company can resolve this for you. however please note that if it is gas related a pressure test must be carried out to determine where that potential leak may be and that can be very costly.
Posted on Nov 14, 2007
Go to www.mrslim.com. In the Customer Resourses file select library. Select what you want for a guide. I suggest the Operation or Technical manuals. Then select Mr. Slim Spli-ductless. Select M-series Multi-Split and the current. You will need the model number off of the outside unit to be able to pull up info on it. It may be a good idea to get the model number off of the ceiling cassette as well. Research what a P8 and E0 code is.
Typically it may mean low refrigerant or a power problem.
Posted on Nov 13, 2007
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 26, 2015 | Mitsubishi MSZ-GE06NA Mr. Slim Wall...
Dec 26, 2012 | Mitsubishi Mr. Slim MXZ30TN Air...
May 26, 2012 | Mitsubishi Mr. Slim MXZ30TN Air...
Feb 05, 2011 | Mitsubishi Mr. Slim MXZ30TN Air...
Aug 30, 2010 | Mitsubishi Mr. Slim MXZ30TN Air...
Jan 15, 2010 | Humidifiers
Jul 02, 2009 | Mitsubishi Mr. Slim MXZ30TN Air...
Feb 16, 2009 | Mitsubishi Mr. Slim MXZ30TN Air...
Sep 30, 2007 | Mitsubishi Mr. Slim MXZ30TN Air...
493 people viewed this question
Usually answered in minutes!