Question about Heating & Cooling
On Heat mode, when blower motor comes on, cool air comes out of the registers and fan is noisy. I think the hi speed comes on instead of the low speed. there are three wires going to the blower motor, Red, White and black. All are connected to the terminal which are marked R W B correctly. Can anyone tell me how to correct this problem? Furnace is a Coleman reverse flow 5600 BTU DGAA 070BDTA Serial No.001115253
Sometimes people replace the blower motors with a higher horse power. Has this motor ever been changed? I believe the original should be a GE motor
Posted on Jan 28, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 21, 2017 | Coleman Heating & Cooling
on Jan 19, 2010 | Heating & Cooling
Jul 20, 2015 | Heating & Cooling
Jan 30, 2013 | Coleman DGAA070 Automatic Hot Surface...
Oct 08, 2012 | Coleman Mobile Modular Home Electric...
Dec 08, 2017 | Coleman Propane Forced Air Heater...
Jan 20, 2011 | Heating & Cooling
May 09, 2010 | Omega Trane Furnace Draft Inducer Blower...
Oct 15, 2008 | Heating & Cooling
176 people viewed this question
Usually answered in minutes!