Question about Air Conditioners
On Heat mode, when blower motor comes on, cool air comes out of the registers and fan is noisy. I think the hi speed comes on instead of the low speed. there are three wires going to the blower motor, Red, White and black. All are connected to the terminal which are marked R W B correctly. Can anyone tell me how to correct this problem? Furnace is a Coleman reverse flow 5600 BTU DGAA 070BDTA Serial No.001115253
Sometimes people replace the blower motors with a higher horse power. Has this motor ever been changed? I believe the original should be a GE motor
Posted on Jan 28, 2008
Tips for a great answer:
Jul 20, 2015 | Air Conditioners
Oct 24, 2013 | Coleman Intertherm Nordyne Miller Furnace...
Feb 21, 2013 | Bryant Cube Series 1 Stage Heat/ 1 Stage...
Oct 08, 2012 | Coleman Mobile Modular Home Electric...
Apr 14, 2011 | Air Conditioners
Jan 20, 2011 | Air Conditioners
Jun 22, 2010 | Air Conditioners
Oct 15, 2008 | Air Conditioners
Jul 18, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
May 20, 2008 | Goodman CKL60AR60 Air Conditioner
167 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: