Question about Goodman Manufacturing Goodman ARUF182416 Air Handler, Multi-Position, Direct-Drive,
Most likely your fan and heat sequencer has welded shut. This is such a common problem that when I walked into the Goodman parts supply house; they just reached down below the counter under their computer and handed me the part. They are supposed to open when it reaches the temperature set point or you turn it off. When operating normally they run for a few seconds to a couple of minutes after powering off. They are a bimetal style(KLIXON) that cool off and open the switch shutting down the fan and strips. It is a simple replacement. Shutoff the power and remove wires from the terminals one terminal at a time and transfer to the exact same terminal on the new one.
Posted on Dec 14, 2014
From what I can gather it seems like a power source error (red wires attached to the transformer) is allowing it to keep running. Another possibility is it could be your speed tap. These are my speculations about what is occurring.
Posted on Dec 11, 2014
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 04, 2010 | Goodman Heating & Cooling
Feb 07, 2010 | Goodman GMS90703BXA Heater
Jan 28, 2010 | Goodman Heating & Cooling
Oct 02, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Aug 12, 2009 | Heating & Cooling
Mar 06, 2009 | Whirlpool LER4634J Electric Dryer
Feb 28, 2009 | Goodman CPLE24-1 Air Conditioner
Jan 15, 2013 | Goodman Manufacturing Goodman ARUF182416...
94 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: