Question about Amana Heating & Cooling
Turn heater on blows only air no heat
The manual reset is a small switch on the computer control board. If that doesn't fix the problem, while you are there, you will see 2 small black boxes wired into the computer board marked "heater 1" and "heater 2". These are relays, one of which has probably gone bad. You can either order a computer board for about $100 or replace the relays yourself with a soldering gun. You can order the relays for $4.02 apiece from Digi-key Corp. Part # is JTN1aS-PA-F-DC5V for the relay.
Posted on Dec 14, 2014
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
It sounds like your blower is coming on before your heat. With gas if your unit is new enough, typically you have an ignition mode to start your heat process, flame recognition, and then full burners, heating up your heat exchanger, and then bringing on your blower. Your blower maybe controlled by a circuit board, just depends upon age of your system.
Posted on Nov 20, 2007
The reset button is located behing a panel on the front of the unit that is labeled Heat Reset. If that label is gone then look around, it is a small hole, small enough for a paper clip to fit through.
That being said, I have 137 of these units in one of my hotels and have not had a single one needing to be reset. You probably are going to need a new control board kit. These can be purchased from Amana. They are $130. Make sure that you have pulled the heater coil out and inspected it first. Also, there was a recall years ago where Amana was supposed to contact and send out new voltage switches. These are the round black things that the Brown heater wires connect to on the upper and lower side of the heating coil. You should also try to replace those if you find the coil in good condition. I have had those resolve heating issues. Most of the heating issues were a result of a bad relay on the control board though.
Please remember to rate this fix.
Posted on Feb 12, 2009
Sounds as though the power cord reset switch might be bad and need to be replaced. If not, then there is a short somewhere in the system. Do an ohms test on the switch to determine if it is bad.
Posted on Mar 17, 2009
Tips for a great answer:
Jul 10, 2015 | Amana Heating & Cooling
May 19, 2012 | Amana DigiSmart PTC153B35AM...
Apr 07, 2011 | Amana DigiSmart PTC153B35AM...
Feb 12, 2011 | Amana PTH153B50AM Air Conditioner
Nov 13, 2010 | Amana PTC123D50AR Air Conditioner
Nov 12, 2010 | Amana PTH153B50AE Air Conditioner
Oct 30, 2009 | Amana PTC153B35AJ Air Conditioner
Jun 14, 2009 | Amana 22.6 cu. ft. Side-By-Side...
Nov 23, 2007 | Amana PTC153B50AJ Electric Heat Air...
131 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: