Question about Pool & Spa
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get 2 Free calls (no credit card required) and instant help on almost anything you can think of (from cars to computers, appliances, handyman, and even pets).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
It could be that the Igniter has gone bad. Or it cold be a number of other items, like the gas valve itself. If the heater has a display panel on it, is there an error code showing? If there is, go to your Owner's Manual and find out what the code is for the heater.
If you do not have a manual, you can find one online at the following link:
Posted on Jul 08, 2009
Do you replace the thermopile or check the milivolts?
Check the Pressure gas
You need replace all of them terminals and check again the milivolts at the gas valve
Posted on May 29, 2010
Problem with the thermocoupler its not producing a minivolt of 250 plus
that is needed to open the main gas valve
Posted on Jun 05, 2010
Tips for a great answer:
Dec 06, 2014 | Pool & Spa
May 27, 2014 | Teledyne Laars Laars Lite 2 Pool Heater...
Oct 21, 2012 | Teledyne Laars Laars Lite 2 Pool Heater...
Jan 28, 2012 | Teledyne Laars Pool & Spa
Jun 05, 2010 | Teledyne Laars Laars Lite 2 Pool Heater...
May 15, 2010 | Jandy Laars Lite 2 Pool Heater 125,000 Btu...
Mar 06, 2010 | Teledyne Laars Laars Lite 2 Pool Heater...
Jan 14, 2010 | Teledyne Laars Laars Lite 2 Pool Heater...
Jun 01, 2009 | Teledyne Laars Laars Lite 2 Pool Heater...
57 people viewed this question
Usually answered in minutes!