Question about Heating & Cooling
Nothing yet thinking does it want a knew wick
Not sure what kind of heater but if it heats with fuel oil your wick is either burnt so it's too short or you have it set too low. I had one a few years ago and had to replace the wick.
Posted on Dec 06, 2014
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get to try the service completely Free afterwhich it costs $6 per call and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
try bringing your wick up to the fully raised position and pinch and bend the wick toward the igniter until they line up right. I have two coronas one of which has a broken igniter due to wear and tear. If you open the little door,press down the start lever,and light the wick with a barbecue grill lighter,you can safely light the heater if lining up the wick fails.
Posted on Nov 02, 2008
take a needle and put it into the end of the gas pilot hole. Wiggle it around in there, it just might have dust build up in there. Hope this helps ya.
Posted on Jan 17, 2009
here is the problems associated with code EE02.
problem cause solution
no ignition: out of fuel check fuel gauge or tank, refuel
fuel tank valve closed open valve turning clockwise
air pocket in fuel line push reset button on the fuel sump, located right inside .
clogged flue pipe clean flue pipe
clogged fuel strainer clean fuel strainer
ignitor,circuit board, consult dealer
flame sensor, or fuel
it sounds like it may be a clogged strainer located in fuel sump or a bad circuit board hope this helps
Posted on Jan 23, 2009
I had to replace the regulator. If you have a propane appliance shop near you, you can probably just get the nipple that goes into the bottle. It's aboit 3/16" diameter, 3/4" long and may have a 6 sided end up inside the screw on cap of the regulator.
Posted on Feb 24, 2009
Tips for a great answer:
Feb 07, 2011 | Coleman Heating & Cooling
Jan 19, 2011 | Reddy R115DT Oil Filled Utility Heater
Dec 27, 2010 | Endless Summer gwt501a Open Flame Patio...
Dec 26, 2010 | Rinnai Toyostove Direct Vent Heater: Laser...
Dec 07, 2010 | Master Heaters B155DST
Jul 30, 2010 | RTO Atwood Water Heater - 6 Gal LP
Dec 24, 2009 | 2001 Dodge Ram 2500 Truck
May 30, 2009 | Coleman (5040B750) Patio Heater
Jan 22, 2009 | Reddy Heater 60,000 BTU Kerosene...
49 people viewed this question
Usually answered in minutes!