Question about Heating & Cooling
How to remove and install
There will be control wiring to disconnect and maybe a molex molded plug or two as well as a portion of the condensing drain connections and trap. Two 5/16" screws should hold the blower assembly in place and once all obstructions are cleared, remove the two screws and slide the entire assembly out. It is mounted on rails.
If you are lucky, there will be enough 'play' in the thermostat wiring to allow it to remain connected and just set aside along with the control box and related wiring.
Once out, remove the square headed 5/16" set screw from the blower motor shaft and remove the motor by disconnecting the three point 'spider' mount. Should take a 3/8" wrench to remove those. Two sheet metal screws then hold a restrictor plate in place at the discharge opening of the blower that must be removed to allow the removal of the blower wheel.
Once done, reverse the process.
Posted on Dec 02, 2014
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 27, 2016 | Heating & Cooling
Jan 22, 2014 | Honeywell ICP Tempstar Heil Furnace Gas...
Oct 17, 2013 | Carrier Icp Heil Tempstar Furnace Blower...
Nov 12, 2012 | Heating & Cooling
Dec 30, 2010 | Water Heaters
Jan 21, 2010 | Heating & Cooling
Jan 02, 2010 | Cross Furnace Draft Inducer Blower 115...
Oct 17, 2009 | Heating & Cooling
Dec 14, 2008 | Cross Furnace Draft Inducer Blower 115...
41 people viewed this question
Usually answered in minutes!