Question about Honeywell Heating & Cooling
Can only get hot water or heating, not both. To get hot water, I have to switch both hot water and heating "off" on the timer controller, then switch hot water on. To get heating to work, i have to again switch both hot water and heating "off" on timer controller, then switch heating on. Timer is Honeywell ST9400c and 3 port valve is Honeywell V4073A.
The first thing you need to substantiate is the fact that there is enough water in the system. It will be a closed loop system requiring approximately 10 psi/ floor. (Only a rule of thumb). Usually when one protion of the system works and the other does not, it is an issue of water quantity available to circulate through the combination of loops. If you have to add water, you will probably have to purge air from the highest points in the system. Even if there is an "Airtrol" fitted in the bottom of the expansion tank, bleeding the high points will eliminate air quicker.
The hot water portion of the loop should only be going through a heat exchanger that transfers the loop temp to the domestic water circuit and the three way valve is probably a 'mixing valve' utilized to maintain a certain loop temperature on the primary loop.
Posted on Jan 08, 2015
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
with y plan 3 connections on programmer HW on HW off CH on HW on to cylinder stat then HW call to Orange on Mvalve to power boiler and pump HW off to grey wire on Mvalve to close hot water CH to room stat common then heating call to white on Mvalve
Posted on Aug 17, 2009
This does not sound like a thermostat problem. I would be looking for a zone valve or circulator pump problem.
Posted on Nov 12, 2009
Depends on type of control system but usually you will have a three-way motorised valve somewhere. This is contolled by the tiimer and the thermostat on your cylinder. Look for a box that has one pipe going in to it and two further pipes coming out. I suspect yours is stuck on heating. Some models had a manual lever to put it to just hot water. End of the fday you need to get someone out to fix this one.
Posted on Jul 22, 2010
Tips for a great answer:
Feb 09, 2016 | Water Water Heaters
Nov 27, 2015 | Water Water Heaters
Aug 17, 2014 | Water Heaters
Dec 10, 2012 | Water Heaters
Oct 19, 2009 | RTO Ariston Gl4.0 Instantaneous Electronic...
Oct 09, 2009 | Audiovox Bosch 718 World Cellular Phone
Nov 01, 2008 | Heating & Cooling
Oct 18, 2008 | Water Heaters
Aug 26, 2008 | Heating & Cooling
115 people viewed this question
Usually answered in minutes!