Question about Honeywell RTH230B 5-2 Day Programmable Thermostat Large
Only not the 5-2, its 7 day but same unit
Try replacing or installing two AA batteries. or call 1-800-468-1502 for help, that number is from the manual you read.
Posted on Nov 26, 2014
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: installing thermastat
any wire can go to any terminal. unfortunately you now have to hand trace each onre to the device it powers and hook it up accordingly. a daunting task even for a pro. having said that the installer could have used the normal colrs for the usual wiring if you were real lucky. as a general rule the red goes to the r terminal. the yellow goes to the y terminal. the white on a heat pump usually goes to w2. the green powers the fan and goes to g. usually the changeover valve is powered by the o terminal and that is usually wired with an orange wire. that only leaves two more wires. one is the auxilliary or emergency heat terminal and any color wire can be used for that. it will go back to the airhandler and tie on to the w terminal along with the white wire from the stat on most units. or they may have jumped the w and emergency terminal together and hooked the white wire to both. it will work either way. that only leaves one wire and that is the common wire to the stat taht allows it to light up and think and have power. . most stats need the red and a common to work. you may have bought a stat that works off battery power only but since you are blowing fuses it seems you have a common pulled on one wire that you have hooked up wrong and it is creating a dead short , aka a blown fuse. if you go to airhandler and finf low voltage terminal board look for terminal labeled comm . observe what color wire is connected to it and if that is the wire that goes off to the stat. if it is hooked to common and goes with the others to the stat then thats your common and should be hooked to your stat common terminal as outlined in your install sheet. you can keep replacing those fuses till you get it right or take a chance and use an amp probe and a jumper wire . only run an instant and if amps are 4, 5, 6, amps at trans your wrong. only test an instant or you will ruin transformer.probably best if you get a box of fuses.label stuff make notes and good luck. i have gotten in the habit of using a sharpie pen to make copius notes right on the service panel for me and the next guy.
Posted on Oct 30, 2008
Hello,You forgot to wire the O terminal w1 witch is the reversing valve.It is important to check if old stat is using O or B in witch case B terminal=w1 leaving O unused.
Posted on Apr 21, 2010
Tips for a great answer:
Feb 17, 2017 | Honeywell Heating & Cooling
Nov 05, 2016 | Honeywell Heating & Cooling
Feb 18, 2014 | Taco Zvc406-exp-4 Boiler Zone Control,6...
Mar 10, 2017 | Heating & Cooling
Jan 27, 2013 | Carrier Heating & Cooling
Feb 06, 2010 | Heating & Cooling
Jan 09, 2010 | Honeywell Programmable Thermostat Heater
Jun 21, 2009 | Honeywell Programmable Thermostat Heater
Jan 29, 2009 | Heating & Cooling
Jan 22, 2009 | Honeywell Programmable Thermostat Heater
Feb 21, 2015 | Honeywell RTH230B 5-2 Day Programmable...
105 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: