Question about Heating & Cooling
24 volts is present at the gas valve, and 24volts at the out put of damper The rollout switch reads ok
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: cozy furnace
The pilot orifice could be dirty causing the pilot flame to be too small. Unscrew the pilot tube at the pilot assembly. The orifice is inside. Remove the orifice and blow it out with compressed air only. Reassemble and see if that fixes the problem. If the pilot flame is set too low, sometimes opening a door will cause a draft to blow out the pilot. If the thermocouple is good and the pilot flame is set properly, the control valve may be bad.
Posted on Feb 05, 2009
I cant see your wire diagram but trace the circut your talking about. I believe it usually goes through a series of safety switches. Put your VOM across each individual switch. If you get 24 out from the board the first 1 you check and get 24v is open and not feeding back to the board is out. FIND out why. the switch could be bad but it may be indicating a more involved problem, just look aroeund for chared wires or tell tell signes of flame roll out or if its an open (fuse link) suspect what can cause an over heat condition anythign from a bad board or too long an off cycle before the indoor fan comes on ect. PONIT IS Once you come across the cause may not be the reason.
Please grade me accordingly and if you need more I need more info from you.
Posted on Mar 02, 2009
Go to www.grainger.com and look for a "power pile generator" this is a millivolt thermocouple that may be just what you need to make your heater work again
Posted on Nov 12, 2009
Turn off the power to furnace.
on the last burner to light there is a small metal rod in front of the burner. This is a safety called the flame sensor. It is dirty. Unscrew it from the bar ( 1 Screw) unplug the connector wire from it and clean it with steel wool. it will be kind of burnt. Plut back in place and turn on the furnace to cycle.
Posted on Apr 04, 2010
Tips for a great answer:
Sep 20, 2015 | Heating & Cooling
Mar 01, 2015 | Heating & Cooling
Jan 01, 2015 | Dryers
Oct 07, 2014 | Coleman 7990-319p Evcon Gas Furnace...
Sep 14, 2014 | Heating & Cooling
Nov 06, 2010 | Heating & Cooling
Nov 06, 2010 | Fedders Heating & Cooling
Jan 10, 2010 | Dayton Gas Furnace Heater
Jan 07, 2009 | Water Heaters
Jul 28, 2008 | Tappan 30IN ELEC IGNa Oven
Aug 19, 2017 | Frigidaire Heating & Cooling
69 people viewed this question
Usually answered in minutes!