Question about LG Heating & Cooling
I have a Lg Multi v heat pump. we had a freon leak, evacuated system and recharged but now can't get any heat or cool out of it. It runs continuously and shows no codes. pipe is really hot next to inside coil up to EEV. 12 indoor units are connected to the outdoor unit and all are doing the same thing. This unit was functioning before the leak but would sometimes show code 32. any suggestions what to try next? The Hvac company may have put sealant in the unit
I'm a retired and certified HVAC&R Technician. You only indicate that you "evacuated the system and recharged it." If that is all you did, then you have problems. Where was the Freon leak? What was done to repair the Freon leak? When you evacuated the system, did you then pull it down to 28 inches of vacuum? If so, did you ensure it held 28 inches of vacuum for a minimum of 30 minutes? Then, did you charge the system with 250 psi of Nitrogen and ensure it held for 30 minutes? If so, did you then release the Nitrogen and pull another 28 inches of vacuum prior to filling the system with Freon? These are the steps I used EACH AND EVERY TIME I EVACUATED A SYSTEM; and I only had a problem ONCE where the copper tubing got extremely HOT and the system would not HEAT or COOL. Found out the reversing valve was stuck half way. Had to replace the reversing valve. Good luck.
Posted on Nov 22, 2014
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get to try the service completely Free afterwhich it costs $6 per call and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
the thermostat sub base has a place to connect a wire usually white to energize the heat strips when you push the stat way hotter than the house temp. that is why the strips come on in normal heat. it also has a terminal that is only energized in emergency heat and it also should have a wire connected to it so that terminal can supply power to the strips when the stat is switched into emerg heat . you can identify the terminal from the wiring diagram and if need be jumper w2 wire over to the aux terminal and it will work. they both go back into the airhandler and power the same strips. w2..................................................................................................w2 in airhandler to strips or w2...jumper to aux......................................................................................................................w2 in airhandler to strips.
Posted on Nov 10, 2008
SOURCE: System will not start up.
This is a signal fault between the indoor and outdoor first make sure the dip switches are set start with the unit closest to the condensor set as unit 1 then next unit as 2 and so on the dip switches are inside the indoor unit on the pc board if you check the manual it will tell you which swithes to set, if this wasnt done when the units where installed they would have never worked i would also check the signal wiring between the wallmount and the splitter box / bc box and make sure there isnt a loose connection when you have ruled this out id say more than likely it is a faulty indoor board on the wallmounted unt
Posted on Apr 08, 2009
SOURCE: LG split (3 indoor) LMU360CE
The LED #2 is only flashing while in disconnection or short in Thermistor (3 sec off / 0.5 sec on). If you want to change it, note: this is not an easy job to do! You will need to remove the top panel, then remove the control paneland then the front panel to gain access to the thermistor. The part isnot available to the public and requires an authorized service techfrom LG to take care of this problem. You will need a special tool toremove the front door seal spring clamp.
But you can call customer service @ 800 243 000 and see if theycan transfer you over to parts. Just give them the model and serial #and see if they would be willing to sell you the thermistor part. Youwill also need the door seal spring clamp removal tool to make the jobeasier.
Posted on Aug 02, 2009
CA: Compressor Discharge Sensor Fault
Contact a qualified service technician and have them replace this sensor.
Posted on May 04, 2010
SOURCE: eo error code
You need a professional here. Once this has been repaired, I would suggest running the wiring to the outdoor unit inside some sort of piping to protect it.
Posted on Jul 21, 2010
Tips for a great answer:
Jul 04, 2012 | 2000 Ford Explorer
Oct 04, 2017 | 1998 Ford Mustang
Aug 18, 2011 | 2000 Saturn SL
Jul 19, 2011 | 2001 Dodge Ram 2500 Truck
Jul 16, 2011 | Mitsubishi Montero Cars & Trucks
Jul 13, 2011 | Windchaser PAC8 Air Conditioner
Jun 30, 2011 | 1995 Mercury Grand Marquis
Jun 11, 2009 | 1997 Cadillac DeVille
Jun 09, 2009 | Dometic Rooftop RV Air Conditioner
May 13, 2009 | 2004 GMC Savana
89 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: