Question about Dayton Heating & Cooling
105,000 BTU, V120, Hz60, Phase 1 Direct Spark Ignition
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Yes, the flame sensor is part of the intermittent pilot assembly. Check the following: make sure all grounding wires are secure and no corrosion is built up on them. Clean or replace the pilot assembly, also clean out the orifice with a very small drill. Make sure the sensor is in the flame and make sure the pilot tube is not leaking gas reducing the gas pressure at the pilot.
If it continues, you will have to replace the ignition control.
Posted on Nov 26, 2007
after you relight have you tried to leave the gas valve on pilot for 10 to 15 minutes so the themolpile warms up enough to send mil-volt signal. you also have a thermocouple that senses flam so if the flame is not hitting that just wright it will shut off. Is this fire place ran off a thermostat or a on off switch. If you are running off a thermostat then i would try to find on/off switch and try that. You might have to change pilot assembly out.If you do this and don't have manual i would take a picture of the log set up so you put it back together. Make sure all connections are tight when you go back together
Posted on Jan 20, 2009
Tips for a great answer:
Aug 20, 2012 | Water Heaters
Sep 21, 2011 | Water Heaters
Aug 24, 2011 | Water Heaters
Aug 16, 2011 | Rheem 50 Gallon FVR NATGAS Water Heater...
Aug 15, 2011 | General Electric Water Heaters
Aug 09, 2011 | Reliance Natural Gas Water Heater Control
Jun 28, 2011 | RTO Atwood Water Heater - 6 Gal LP
Feb 06, 2010 | Dayton Gas Furnace Heater
Oct 24, 2009 | Reddy HEATER RLP30 30,000-BTU PORTABLE LP...
Nov 26, 2007 | Dayton (3E379) Heater
64 people viewed this question
Usually answered in minutes!