Question about Goodman Heating & Cooling
The only reason water would come out of your furnace is if you also have your AC in the same system, and the condensation line is not allowing the water to drain properly.
If the water only happens during cooling, clear the condensation line. If it is happening during a heating cycle you may have an improperly connected thermostat, a bad control board, etc...
Posted on Nov 17, 2014
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
You need to type GOODMAN GAS APPLIANCES into you browser to find you local servicecenter. I must tell you that Goodman only sells to authorized service companies in my experience. So you become EgKraft Company.
Posted on Nov 07, 2008
I have a goodman GMP075-3 that won't turn on. I think it is the pressure switch since I do not have a vent blockage. What is a venter and where can I find it??
Posted on Dec 30, 2008
You have a limit switch located in the furnace (a little bigger than a dime and located near the center of the front panel, sometimes the switch is mounted to a small fiberglass board) . There will be two wires going to it. They sometimes trip so often that they fail to automatically reset(due to dirty filters or undersized ductwork). You can SHUT OFF POWER TO THE FURNACE, then remove the two screws holding the switch in the furnace, pull the switch out of the furnace and tap on it and wipe it off.
The switch may work a few more times but should be replaced with the same size and type. You will see some rating printed on the switch somewhere. Write down all the numbers and get a replacemet from a furnace/AC supply house. If you have a meter and know how to use it you could check the switch for continuity.
Sometimes just a tap on the switch will get it going. There will also be a couple of rollout switches that could be tripped. They have little buttons on them to reset them. If they trip it may have other issues to be solved.
Hope this helps!
Posted on Feb 01, 2009
I have a forced air gas furnace and water is leaking from just above the area where the hose is attached. I removed the cover but cannot figure this out. It only leaks (a lot of water) when the furnace is running. Please help asap!!! Tthanks so much, Dianne
Posted on Jan 03, 2010
Tips for a great answer:
Jan 04, 2016 | Goodman Manufacturing GCH950904CX 95% AFUE...
Jan 24, 2008 | Goodman GMS90703BXA Heater
Nov 17, 2014 | Heating & Cooling
Dec 26, 2012 | Goodman Heating & Cooling
Feb 08, 2010 | Goodman CLQ36AR49 Air Conditioner
Dec 11, 2009 | Jandy Lite2 LJ125 Ceramic Gas Heater
Oct 13, 2009 | Goodman GMS90703BXA Heater
Jun 09, 2009 | Heating & Cooling
Nov 23, 2008 | Goodman GMS90703BXA Heater
293 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: