Question about Pool & Spa
It is not heating pool, help.
If water is flowing thru the panels/collectors, (look to see if the valves are opened to allow water to the collectors) if the water is flowing and it is flowing through the collectors/panels, then the water is being heated!
If you are saying the controller is set for solar operation and the sun is shining, and there is a "Demand" for heat or a "Call" for heat, and the Valve is NOT turning to allow the water to the panels, then you have a problem with either the Hayward/Goldline Controller or the Valve Actuator.
Posted on Nov 27, 2014
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
hello, It sounds like you may not be getting circulation thru the heater. Make sure the valves are open to allow water to pass thru the heating system. Some systems use a bypass on the heater so there is not a lot of wear on the coil system in the heater. If it is not circulating it will get too hot and the safety shut down will occure. If you are getting water circulating thru the heater, then the thermocouple or auto start igniter system is not working correctly. It is trying to start and can't then recycles. If the burners are igniting on the startup and then shutting back down you may have a bad control unit or thermal sensor unit. Since the unit is gas have a professional service it for you. Good Luck, RAC
Posted on Apr 20, 2009
Check the valve actuator toggle switch. It is 180 degrees out. If the toggle switch is in the up postion flip it down or vise versa.
Posted on Aug 30, 2009
SOURCE: error code 126
This is a bad thermister or heat sensor. It mounts in your water manifold and if it goes bad no error will show. The bad sensor is telling the heater that the water is to hot and it wont let the heater fire. This is a farley inexpensive part and easy to change out. With a new one it should read the proper temp and call for heat then fire the heater. Good luck.
Posted on Dec 08, 2009
This could be a bad thermostat or temp sensor, or it could be a water flow problem. Ether the by-pass in the heater or on the outside pipes. It could just be the filter is dirty expecally if it is a DE filter. These should be taken apart and cleaned at least once a year. I hope this helps.
Posted on Dec 10, 2009
Tips for a great answer:
Jul 17, 2015 | Goldline Controls GL235 Solar Controller...
on Dec 12, 2009 | Heating & Cooling
Nov 15, 2014 | Goldline Solar Pool Control Package Gl-235...
Mar 03, 2014 | Goldline Solar Auto Controller GL-235
Apr 17, 2013 | Goldline Solar Auto Controller GL-235
Mar 24, 2017 | Fafco Deluxe Solar Panel Heating System 1...
May 25, 2010 | Fafco Deluxe Solar Panel Heating System 1...
Nov 28, 2009 | Frigidaire 30" Self-Cleaning Freestanding...
Nov 08, 2009 | Solar Heating System For Swimming Pools
Sep 02, 2009 | Solar 2 PANEL DELUXE SOLAR HEATING SYSTEM-
141 people viewed this question
Usually answered in minutes!