Question about Cfm Klimaire KSWG009H113 Split System Air Conditioner
I have a klimaire mini split.when it was installed there was a screw in the electrical panel box that penetrated the feed wire and caused the breaker to trip however after repairing the wire the condenser does not start. the inside blower unit does work. any suggestions?
Check for correct voltage to unit short may have burned out breaker .
Posted on Nov 30, 2014
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
for this you have to go into the the board located in the right side of the unit if your problem is what i think it is crosswire on the board.
Posted on Jun 03, 2010
Tips for a great answer:
Oct 21, 2013 | Klimaire Heating & Cooling
Sep 02, 2013 | 18,000 BTU KSIM DUCTLESS MINI SPLIT...
Mar 23, 2013 | Heating & Cooling
Jun 18, 2011 | Square D Co. QO612L100S Main Lug Load...
May 14, 2011 | Electrical Supplies
May 11, 2011 | Challenger Circuit Breaker
Jun 02, 2010 | Cfm Klimaire KSWG009H113 Split System Air...
Nov 22, 2008 | Fahrenheat Electric Convector Baseboard...
96 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: