Question about Hardware & Accessories
It has a green wire; I assume this is the ground, no problem. It has a black one and that is the hot wire, no problem, but what does the blue one go to? Which white wire in the socket? The white and black wires (two of each color) are wrapped around a different nut and separated. I picked a single pole outlet, so it would work. HELP! Thanks
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
HI .. if the switch has only a black and white wire attached, and there are no other wires in the wall box, then you cannot use this timer switch. You need to return it and get a timer that does not use a neutral connection. The wires you have are a switch leg from the light and there is a white wire but it is not a neutral.
If there are other wires in that wall box , tell me and we can chat more about how to remedy this .
Please Vote !!
Posted on May 25, 2010
Find the Hot wire:
Your switch has 2 wires. One of these wires is Hot, and one goes to load. Disconnect wires from switch. Turn on power. Do not stand on wet surface. Test each wire to bare copper wire. When tester lights up, that is Hot wire. The other wire goes to load.
Hot wire goes to Black timer wire
Wire to load goes to Red timer wire
White wire connects to white wires that are twisted together
Bare copper wire connects to Green wire from timer
How to connect white wire to white wires that are twisted together.
a) Strip white timer wire so you have 1-1/2 " of bare wire. Stranded wire will wrap around other wires easily.
b) Remove wire nut. DO NOT UNTWIST wires.
c) Hold all whites together so bare copper lines up. Wrap stranded copper around the twisted wire.
d) Replace wire nut, or use larger wire nut. Twist real tight. Do not use tape. You can solder the connection.
e) When done, pull on white time wire to make sure it is held tight. Push whites back into box.
Posted on Sep 26, 2010
SOURCE: am replacing an old wall
I've tested these timers.
Here's what to do:
1) Connect green to bare copper
2) Switch has 2 wires. For now, connect these two wires to timer-black and timer-red. Choose either one.
3) In back of wall box are white neutral wires twisted together and covered with wire nut. Timer-white wire connects to these white neutral wires. This action gives power to time clock.
4) If wall box does not have white neutrals described above, then connect timer-white to bare ground wire. Bare ground connects to neutral busbar in breaker box.
5) Turn on power and click manual override button or switch. If lights turn on, timer is wired correctly. If lights do not turn on, then reverse timer-red and timer-black wires.
Posted on Nov 16, 2010
Connect all three white wires together. This passes the neutral through and it provides the neutral to power the timer's clock. Connect the black hot wire to the black on the timer. Connect the black going out of the box to the blue on the timer. Connect all grounds together. If that doesn't work, trade the two black wires. good luck Al K
Posted on Dec 14, 2010
SOURCE: I bought a Utilitech Self
The reason there is 2 black in the wall is because a standard line breaking switch was used. Meaning the hot side of the light was the black wire once broken light goes off. You would hook the black from switch to black in wall and white from switch to other black in wall green is ground and red put wire nut on. Red is for a 2 switch system. Where one of two switches in same room controls same light. Its not needed. Take caution when doing this trun light on goto breaker box and flip breakers till you find the right one that powers that light. once lights off then do your thing replacing.
Posted on May 06, 2011
Tips for a great answer:
Sep 03, 2011 | Intermatic & Self-Adjusting Wall Switch...
May 06, 2011 | Intermatic Inc. ST01C Digital In-Wall...
Apr 17, 2011 | Intermatic & Self-Adjusting Wall Switch...
Dec 11, 2010 | Woods Hardware & Accessories
Nov 16, 2010 | GE 60minute Automatic ShutOff Timer Switch...
Oct 17, 2010 | Intermatic Inc. ST01C Digital In-Wall...
Oct 03, 2010 | GE Electrical Supplies
Oct 01, 2010 | Solar Ivory Swylite Lst100+ Back-lit...
Sep 11, 2010 | Intermatic EI210 Electronic Auto Shutoff...
Apr 08, 2010 | Intermatic Inc. EJ500C Digital Wall Switch...
54 people viewed this question
Usually answered in minutes!