Question about Heating & Cooling
It may be possible to drill it out and glue a slightly smaller hose up in side it .
Posted on Nov 13, 2014
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Whirlpool Air Con Drainage issue
Yes, there should be a place for the condensate to drain outside. It's apparently clogged and the drip pan is overfilling. Look for a tube or an opening outside where the condensate should be exiting. This needs to be unclogged.
Posted on May 31, 2009
try lifting the unit off the wall and making sure its level and flat against the wall so the water flows as it should in the tray
common install related problem
Posted on Jul 05, 2010
SOURCE: water is backing up and
The water dripping from evapourator is due to clogging of the cooling pins.where in the condensed water logs into the front portion into the filter,the front pannel and to the wall.If the unit is slightly tilted, this would be reduced.use a good brush and air pressure to clean the fins.If periodical cleaning of the filter is not done,this can happen.
Posted on Sep 02, 2010
The water is being generated from humidity inside the air. The air conditioner also acts as a dehumidifier. The black line is the drain. The drain line needs to go to an outside line or to a container to collect the condensated water. With low humidity levels, the water will evaporate back into the air. With high humidity, the water is removed from the air at a higher volume than can evaporate back into the air.
Posted on Jan 29, 2011
Tips for a great answer:
Aug 23, 2014 | Home
Feb 15, 2013 | Washing Machines
Feb 21, 2012 | Whirlpool GU2400XTP Built-in Dishwasher
Jun 25, 2010 | Goldstar KG6000R Window Air Conditioner
Oct 07, 2009 | Mitsubishi Heating & Cooling
Jul 26, 2009 | Bosch Dishwashers
Jul 14, 2009 | Maytag M7DH65B2A Dehumidifier
Feb 03, 2008 | Bosch Logixx WFT 2806 Front Load...
Nov 21, 2017 | Heating & Cooling
32 people viewed this question
Usually answered in minutes!