Question about Heating & Cooling
Model # AZ29E12DABM1
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get to try the service completely Free afterwhich it costs $6 per call and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Heat pumps have saftey circuits that prevent liquid flooding of the compressor. Inadequate airflow across the evaporator in cooling can trip this circuit. Have your package unit serviced with particular attention to cleaning the evaporator coil and be sure your filters are clean and changed frequently in the summer months. Hope this helps GL!
Posted on Jun 08, 2008
Do you have gas or electric heat. If you have gas then you do not have a heat pump. You should in most cases have a red,yellow, white, and green wires coming to the thermostat. R should go to rc/rh G should go to green Y should go to Y and w should go to W. Also the switches on back should be switched to non heat pump and gas rather than electric. Hope this helps.
Posted on Feb 16, 2009
It sounds like you have a refrigerant leak. If both coils are clean and air fiter is clean nad you can hear compressor running, most likely refrigerant leak. If this unit has heat strips verify they are not running during cool mode.
Posted on May 22, 2009
If the a/c fails to continue to blow cold there could be a few problems you can look for. First once you activate the system check to see if the compressor kicks in. You will hear the compressor humming . Once the a/c quits cooling go and see if the compressor is still running. If its not running its probibly gone into thermal overload (compressor overheated). If that is the case then you need to check to see if the coils are icing up if they are icing up then the problem is with 1) air flow restriction filter dirty, coils dirty simple repairs there replace filter, clean evaporator coil with a coil cleaner that can be purchased at a home repair store cleaning the condensor coil the same. 2) system is low on freon in which case the system will need to be recharged. Also, If you have a digital thermostat replace the batteries that may also be of some help. Good Luck on repairs
Posted on Aug 31, 2009
Tips for a great answer:
Jul 19, 2016 | Winchester Model 94 Short Rifle .30-30 20...
May 24, 2016 | Optics
May 22, 2016 | Optics
Jan 22, 2016 | Winchester Optics
Jan 03, 2014 | 4-Seasons 2004 Chrysler Intrepid Fan Motor
Nov 13, 2013 | Kia Cars & Trucks
Dec 29, 2012 | Dryers
Nov 12, 2012 | Heating & Cooling
Oct 20, 2012 | Cars & Trucks
45 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: