Question about Kitchen Appliances - Others
Everything else seems to be working and I have no error lights on the control board
Check the fan control switch. The switch closes at 240 PSIG. Then fan comes on. The switch opens at 190 PSIG. Then the fan will cycle off until presser rises. Check to make sure you have power to the switch while in freeze cycle if you do then check the other side ow switch to make sure you have power going through switch if not then either switch is bad or you are low on refrigerant. The switch part number is 11-0479-21. either way if switch is bad or low on refrigerant the refrigerant will need to be recovered and switch will need to be removed and sweated back in and a vacuum pulled and charge weighed back in. Do not replace the control board.
Posted on Nov 11, 2014
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 21, 2014 | Hoshizaki Freezer Commercial Ice Machines...
Jul 03, 2013 | Frigidaire FRS3R5EMB Side by Side...
Jul 10, 2010 | Hitachi Televison & Video
Jan 23, 2010 | Maytag MMV4205 Microwave Oven
Jul 24, 2009 | Jenn-Air 21.6 cu. ft. Side-By-Side...
Jun 01, 2009 | Fujitsu Heating & Cooling
Mar 13, 2009 | InFocus ScreenPlay 4805 Multimedia...
Oct 30, 2008 | Sub-Zero 650 / O Bottom Freezer...
49 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: