Question about Electrical Supplies
What you wish to do is called "piggy-back" 1st mahe sure no pwer is going to existing outlet .2nd. attach wires same color as black is "hot" white is "nuetraul" and green is "ground" make sure all connections are tight.if your running this extra wire to a new outlet then wire in same manner. always double check your connects are correct and tight.once your extra outlet is in place, turn power back on and test ,
Posted on Dec 31, 2014
Bad Idea. Don't do it.
Posted on Nov 09, 2014
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 27, 2014 | Connecticut Electric Electrical Supplies
Sep 20, 2014 | Electric Electrical Supplies
Apr 29, 2014 | Whirlpool GY397LXUS Stainless Steel...
Sep 25, 2013 | Arrow Cooper Wiring TR7735V-BOX Arrowhart...
Jul 27, 2013 | Electrical Supplies
May 17, 2010 | Grilling
Nov 20, 2009 | Electrical Supplies
Sep 19, 2009 | Kitchen Appliances - Others
Sep 02, 2009 | Sport & Outdoor - Others
Aug 28, 2009 | 3M GFI Software GFI MailEssentials For...
63 people viewed this question
Usually answered in minutes!