Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get 2 Free calls (no credit card required) and instant help on almost anything you can think of (from cars to computers, appliances, handyman, and even pets).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Ok, you either have a inducer fan issue or a pressure switch issue or a plugged vent pipe. The inducer turns on to establish a draft for the exhaust. If it is not working you will get this error code. If the pressure switch does not sense pressure caused by the inducer, it will give this code. If either the intake pipe or exhaust pipe is blocked (even y just a little) it will give you the same error code. If the condensate hose or receptical is plugged, again it will give you this error code. Good Luck!
Posted on Oct 21, 2008
On a call for heat, the 24 volt thermostat sends a signal to the control module. The control module will indicate a call for heat with a light on the control either blinking or remain solid depending upon model. The inducer (exhaust) blower will purge all gasses from the furnace and pressurize a pressure switch. Once the pressure switch tells the module to continue, the electronic ignition will energize and send 120 volts to the igniter. The igniter will glow and you will be able to see it if viewed thru the small inspection port. Once the igniter gets hot enough, it sends a signal to the module opening up the gas valve (24 volts). Either a pilot will come on or the burner tube will ignite then spread the flame to all burners. Lastly a safety sensor will be looking for a certain temperature within a few seconds and the furnace will continue to operate and the room air blower will turn on in a minute or two.
What could go wrong? The unit will not run if there is no signal from the thermostat (bad thermostat or broken wire), the control module does not sense a signal from the thermostat (bad control), the inducer does not energize (bad motor), the pressure switch does not close (blocked vent piping, bad switch, plugged condensate hose), the igniter does not energize (bad control, bad igniter), the gas valve does not open or there is no gas (bad gas valve, broken wire, no gas), the pilot does not light (dirty pilot), the burner does not light (bad burner, plugged orifice, not enough combustion air), the flame does not spread to each burner (bad flame spreader, dirty flame spreader, more bad burners), the flame safety sensor does not detect flame (dirty or bad flame spreader, bad flame sensor, broken wire, bad control), or the room air blower does not energize (bad fan motor, bad control).
Your furnace has a diagnostic chart on the reverse of the lower panel incorporated in the wiring diagram. One blink tells you that it is a failure but wont tell you where to start looking.
Posted on Nov 28, 2009
SOURCE: furnace shuts off
Defective combustion air switch. The 3 blinks are an error code. You didn't say, but I'm guessing you have a Coleman Evcon. They had alot of defective Combustion air switches. Your specialists were not that.
Posted on Dec 30, 2009
sounds like it is the pressure switch try jumping it out on some models you fool the heater in too working or see if the tubes are blocked , there should be some codes on the front panel or the fan panel
Posted on Apr 27, 2010
Tips for a great answer:
Dec 05, 2016 | Heating & Cooling
Jan 23, 2016 | Heating & Cooling
Nov 21, 2015 | Heating & Cooling
Oct 03, 2015 | Cars & Trucks
Dec 21, 2012 | Heating & Cooling
Nov 26, 2012 | Heating & Cooling
Apr 27, 2010 | Coleman Propane Forced Air Heater...
Mar 12, 2010 | Heating & Cooling
Oct 13, 2007 | Filter Queen Defender Air Purifier
347 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: