Question about Amana Distinctions 95% Gas Furnace Gmh950704cx 69k Btu
I am handy with tools and electronics as I own a computer repair store.
If you have a variable speed motor The black wire going to the contactor relay is highest speed.or if there is a terminal strip near the motor there will be one wire and three places to plug a wire marked H, M, Low
Posted on Nov 10, 2014
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Amana PTAC
Sounds like if this is a heat pump, maybe it tripped out on high pressure. Maybe just unplugging the system may reset the control boards. This maybe due to a dirty filter or dirty evaporator coil.
Posted on Nov 18, 2007
SOUNDS LIKE YOUR HEAT STRIP IS NOT COMING ON THERE COULD BE A NUMBER OF THINGS TO CAUSE THIS,BAD RELAY ON THE BOARD BAD HIGH HEAT LIMIT,BAD T-STAT
Posted on Dec 01, 2007
as a general rule the lemon law does not effect acs. because the equipment colud be at fault, or the installer couild be at fault , or the installation or application coiuld be at fault, or the power company could be at fault or the ductwork inadquete or undersized? so there are so many variables that a new ac may not fix your problem so they rarely ever provide new.now lets discuss your insatller or dealer. why are they saying the rev valve is bad? let me say covs Changeover valves usually do one of three things. they stick in cool and wont shift so youare stuck in cool or sruck in heat. when energized you hear no kawhoosh sound and compressor doesnt change pitch. then they are stuck in heat or cool. what they do sometimes is stick halfway and that gives a coolish suction and a coolish line to the house but not real cold. the hot gas line is only warm and the discharge line is onlty warm. this means its stuck halfway. some times you can disconnect the fan run the pressures way up and gently tap the valve and it will free up. but it nay stick agagin. the valves in the compressor may also be weak and be misdiagnosed as as half stuck covalve.. you could close off the liquid line and see if the compressor cah pump down to zero . if it can't then compressor maY BE BAD .when the unit was installed did they put in a liquidline drier to collect impurities and protect the valve? its pretty unusual to see a valve fail and if to much heat is applied on replacement then new valve can be damaged. good luck , oh you have the option of requesting a different dealer if it is brand name like trane or american std with a parts and labor warranty. most dealers can honor the other guys warranty and get paid by the factory if you have lost confidence in your guy. i am sure you know right away if you got a budget jack leg job or a pro . good luck.
Posted on Oct 24, 2008
SOURCE: Amana Gas furnace, Air Command
Buy a new ignitor here; The Ignitor Store. Or talk an Amana dealer/Contractor to sell you one. They can range from 15 to 35 bucks! Depending on their mark-up. Give them your model number, and or ignitor part number. Their simple to change out, good luck, please contact if you have any questions.
Posted on Dec 02, 2008
Tips for a great answer:
Dec 15, 2015 | Amana GMH81405DN 140,000 BTU 80% Gas...
Feb 11, 2015 | Amana Heating & Cooling
Oct 28, 2013 | Heating & Cooling
Jan 01, 2013 | Amana Distinctions 95% Gas Furnace...
Jan 09, 2010 | Heating & Cooling
Jan 02, 2010 | Heating & Cooling
Dec 30, 2009 | Heating & Cooling
Dec 26, 2009 | Honeywell Electronic Programmable...
Nov 27, 2008 | Heating & Cooling
73 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: