Question about Teledyne Laars Laars Lite 2 Pool Heater 250,000 Btu / Natural Gas
Here are a few things to check: Does the pilot light stay on after you light it? If so, good, did you turn the control valve to the "on" position? Sounds funny but there's a pilot position and a "on" position. Is the pump on? Water must be circulating through the heater to activate a pressure switch & then the burner will come on. If not find the manual on position for your pump timer to start the pump. Burner still doesn't come on? Check the burner assembly for plugged orifices (i.e. spiders, corrosion, etc.)and clean it out
here is laars installation manual
back with result
Posted on Jul 04, 2009
This water heater relies on a circuit board that provides a spark to light the flame when the switch is placed to the on position. Electrodes sense the flame within six to eight seconds, if the signal is not found the circuit board will shut down the gas valve and the system goes into safety lockout. There is a thermal shutoff that should trip when the temp rises above 190F. This fuse is located on the incoming power wire connected to the thermostat, you should see this under the exterior cover, the ones I have seen have clear plastic on the wire, once they trip they need to be replaced. AT this point I would pull the cover off the exterior, check all the 12 volt wiring make sure there is no corrosion. I would suspect the thermal shut off is bad. IF you have a volt meter you can check for continuity through the fuse. I ran into this not long ago and with this fuse not working it caused the water heater not to fire.
Kindly rate the answer
Posted on Jul 04, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Dec 05, 2016 | Heating & Cooling
Jan 16, 2015 | Williams Wall Heaters: 35,000 Btu/hr...
Nov 28, 2013 | Hayward H Series Pool & Spa Heater 400k...
Aug 09, 2013 | Water Heaters
Jun 20, 2013 | Heating & Cooling
May 28, 2013 | Water Heaters
Nov 25, 2012 | Kitchen Ranges
Feb 19, 2011 | Williams (5009622) Ceramic Gas Wall...
Feb 04, 2010 | Napoleon 36" Zero Clearance Top/Rear Vent...
Oct 29, 2009 | Heating & Cooling
68 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: