Question about Ruud UAMB Air Conditioner
Fan motor not runing I have two caps and dont know which one is run/or start
First pull the quick disconnect (power source). If you have a multimeter with capacitor check (uf) capabilities, look at the side of the capacitor and see what the uf rating is, (should be somthing like 3.5uf or 5.0uf or7.5uf) then stick a screwdriver between both contacts where the wires are pluged into the top of the capacitor and touch both contacts at the same time to discharge any stored electric power, then remove all the wires from the top of the capactor, switch on the multimeter and set it to the uf setting, now place one lead on one side and one on the other, if your capacitor is say a 7.5uf and the reading is 9.0uf or 6.0uf it's bad replace
the capacitor. check both of your capacitors the same way, oh mark your capacitor and the wires so you can put them back together rite. If you don't have a multimeter with capasatence checking capability take them to an appliance shop and let them do it for you.
Posted on Jul 03, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
May 23, 2018 | Coleman Heating & Cooling
Aug 06, 2011 | Heating & Cooling
Jun 22, 2010 | 1996 Buick Park Avenue
May 08, 2010 | Coleman Mach 15 Air Conditioner
Jul 09, 2009 | Heating & Cooling
May 01, 2009 | Coleman Mach III Air Conditioner
Jul 22, 2008 | Weather King 10AJA2501AH Air Conditioner
Oct 25, 2007 | Heating & Cooling
Aug 08, 2013 | Ruud UAMB Air Conditioner
166 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: