Question about Heating & Cooling
Check cooling coil(in door unit)if there ice buil up then feel air vent if no air mean your fin block aready need to clean / air vent ok meant there have a leak .you need r22 test gauge and hose,reamer,tube cutter and flaring kit. 1)check suction pressure(big tube at out door unit) remove 2 way cap and 3 way cap valve then connect blue hose at service port 3 way valve (port locate at left or right depent on manufacturer) you will get pressure about 40-45 psi(air cond is running) then use a allen key(hexagonal wrench) to close 2 way valve(small tube or gas discharge side) wait 1-2 minute then close 3 way valve (suction tube or big tube) IMMEDIATELY SHUT OFF AIRCOND AND PLUG OUT POWER CORD (you need 2 person one at in door unit and the other at out door unit). this method is to keep remaining gas inside the compresser.Then leak check ,open 2 way valve about 90 degree hold it for 10 minute then close it .MEASURE THE PRESSURE keeep it for 5-10 minute. If the pressure indicate not same during the first time measured it meant there have a leakage, for air cond 1- 5 year the leakage will happen at the copper tubing connection and improper flaring .Then U need to clean in door and out door unit ,used a spanner or wrench to losen the copper FLARE NUT at out door unit and in door unit( inside insulation) then use pvc tape to cover all copper pipe/tube hole to prevent dirt go inside tube/pipe. Then lift up out door unit and used coil cleanner ditergent wait 5 minute then flush with water. Remove indoor front panel then disconnect out door unit cable at front panel in door unit then lift up indoor unit to disangage the hook and pull out the indoor unit, then clean the cooling coil ,cover electrical part with plastic .last step u need to cut (used cooper cutter)the copper pipe/tube FLARE NUT connection low side(big tube) and high side(small tube) in door connection and out door connection .Then u need to remove the burr from cut edge using reamer make sure metal powder not goes in Then make a flare after inserting FLARE NUT onto the copper pipes Then U can install back the unit check the low side pressure if the pressure 55-67 psi no need to charge
Posted on Mar 23, 2010
Hook up your gauges to the unit charge to proper super heat and sub cooling Or to that data plate specs. oh ya purge all of your hoses of air I call somebody with a license and have it properly serviced. Tom
Posted on Jul 03, 2009
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 02, 2015 | Cameras
Nov 09, 2012 | Motorola Mobility SLVR L7 Cellular Phone
Mar 04, 2010 | Vidal Sassoon Health & Beauty
Aug 23, 2009 | Audio Players & Recorders
Jul 03, 2008 | 1998 Ford Explorer
Feb 08, 2008 | Audio Players & Recorders
8,901 people viewed this question
Usually answered in minutes!