Question about Kenwood KW85 Air Conditioner
Whether its heating or cooling it runs for about 30-40 minutes and shuts off If I turn control to off then back on it will come on and run for about same time again then shut off. I've had 2 HVAC companies come and look at it first one cleaned the coils same problem 2nd outfit said they couldn't find anything that would cause this.
Start the unit and check unit data ( suction pressure, discharge pressure, current reading voltage reading, check if no icing at compressor suction pipe and evaporator coil) if everything is normal. check the fallowing.
- check for out of range pressure switches. By pass pressure switches and start the unit if the unit continue to run check which of the pressure switch is open while the unit is running.
- check for defective timer and magnetic contactor or control rely.
- if the unit installed with freeze up sensor then check it also.
- Or the control by itself.
Posted on Dec 30, 2007
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 31, 2015 | 2001 Dodge Caravan
Sep 16, 2017 | Heating & Cooling
Jan 28, 2013 | Honda Accord Motorcycles
Feb 26, 2018 | Rival Heating & Cooling
Aug 02, 2011 | Carrier YC273D Air Conditioner Window/Wall
Jan 31, 2011 | Dayton Gas Furnace Heater
Apr 03, 2010 | Dometic Rooftop RV Air Conditioner
Dec 12, 2009 | Heating & Cooling
Dec 15, 2008 | LG LP120HED Wall/Window Air Conditioner
Jun 19, 2008 | AEG B1180-4 Electric Single Oven
103 people viewed this question
Usually answered in minutes!