Question about Whirlwind FH-778 Air Conditioner
HI, MY AIR CONDITIONER IS BLOWS COOL AIR WHEN I FIRST TURN IT ON THEN IT JUST BLOW OUT WARM AIR
Is the outside unit running? if so can you feel warmer than outside air blowing from outside fan? If not your system may have a leak and pressures low. You can also check the piping to and from the unit larger one should be cold small one should be warm
Posted on Jul 26, 2009
Not only "is your outdoor unit running" Is your compressor in your outdoor unit runnning. I've seen people make mistakes thinking that just
because the condenser fan is running that the compressor is too. It sounds like the compressor is shutting down due to overload (hight pressure). The way to know would be to pull power to the unit, then take the door off restore power and listen to see if not only the fan turns on but the compressor also. If the compressor is very hot to the touch and is not running, again turn off power to the unit and run a hose over the compressor. for a few minutes until it is cool to the touch. Restore power and see if compressor starts. If it does the problem could be a dirty outdoor coil (clean it with a hose). If that doesn't solve it, call a tech.
Posted on Jul 29, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 18, 2014 | DeLonghi PAC C120 Portable Air Conditioner
Sep 01, 2011 | Fedders A6X05F2D Air Conditioner
Sep 01, 2011 | Heating & Cooling
Jul 16, 2011 | Heating & Cooling
Jul 12, 2011 | Goldstar R5050 Air Conditioner
Sep 27, 2010 | GE Profile ASM10AA Air Conditioner
Jul 08, 2010 | Continental CE-PAC1163 Air Conditioner
Jan 11, 2010 | Ruud UBHC Air Conditioner
Dec 04, 2009 | Amana PTH153B50AJ Heat Pump Air...
Apr 27, 2009 | Bryant 462AJC021BA Air Conditioner
432 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: