Question about Ruud Matching Split Air Conditioner
You need a volt ohm meter that will check uF, or a meter specific for capacitors. a lot of fans require a 5uF capacitor. they are very cheap to buy. If your fan gets hot, but doesn't start and the blade turns freely then its probably your capacitor is bad. Just kill all power to outdoor unit and pull the leads off on the common and fan on the capacitor and hook them up to the new on and the fan should start.
Posted on Aug 15, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Aug 31, 2017 | Heating & Cooling
Feb 03, 2013 | LG LS-L1210CL Mini Split Air Conditioner
Oct 01, 2011 | Ruud UBHC Air Conditioner
Jul 02, 2011 | Amana Heating & Cooling
May 09, 2011 | Weather King 10AJA3601AH Air Conditioner
Apr 25, 2011 | Frigidaire FAC126P1 wall/window Air...
May 21, 2010 | Heating & Cooling
Jul 01, 2009 | Heating & Cooling
Jul 22, 2008 | Coleman Mach 15 Air Conditioner
Jul 02, 2008 | Coleman Mach 15 Air Conditioner
121 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: