Question about Ruud Matching Split Air Conditioner
Check fan capacitor,disconnect capacitor and measure it with ohm meter,put value on ohm meter ohm x100 or more,measure capacitor
it must show some value but it will be very fast,if there is no value change a capacitor,a new must have same parameters(values) as old
e.g. 80 micro F,220(110,380)V.Note a wire which was on capacitor.
If not capacitor,check fan motor,also with ohm meter,measure all wire for each other,ohm meter must show some value,e.g. 25 ohm.
DISCONNECT air conditioner FROM ELECTRIC POWER WHEN YOU WORK THIS,AND BEFORE MEASURING CAPACITOR SHORT CUT IT WITH A ISOLATED SCREWDRIVER!
Posted on Jul 02, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 19, 2013 | Dryers
Mar 27, 2012 | 1997 Chevrolet Cavalier
Jun 24, 2010 | Broan-NuTone ATTIC FAN THERMOSTAT CONTROL
May 31, 2010 | 2004 Dodge Ram
May 12, 2010 | Honeywell Programmable Thermostat Heater
Apr 30, 2010 | 1999 Jeep Grand Cherokee
Mar 18, 2009 | 2003 Pontiac Sunfire
Oct 31, 2006 | GE JVM1840 Microwave Oven
172 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: