Question about Heating & Cooling
Check for proper voltage at contactor, check capacitor, motor might be going out on overload. Meaning it is getting hot and shutting off. when it cools down it starts again. windings in motor are probably going bad.
Posted on Jul 02, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 07, 2014 | Carrier Heating & Cooling
Jul 15, 2012 | Haier Heating & Cooling
Jun 12, 2010 | Carrier 38CKC042 Air Conditioner
Aug 15, 2009 | Heating & Cooling
Jul 26, 2009 | Heating & Cooling
Jul 20, 2009 | Amana ABC2037SS Air Conditioner
Jul 05, 2009 | Heating & Cooling
Jun 28, 2009 | Heating & Cooling
Jun 12, 2009 | Goodman CLT36AER36 Air Conditioner
May 28, 2009 | Goodman CKL60AR60 Air Conditioner
126 people viewed this question
Usually answered in minutes!