Question about Movincool Classic Plus 26 Air Conditioner
The air conditioner have water runs into the plastic container and when the container is full of water the weight will switch off the whole unit until you empty this container.
The tube that deliever the water into this plastic container blocked up with dirt that stop the water runs into the container and overfill the condenser drain pan that water runs all over the floor. Clean this condenser pan outlet and the connecting tube then you will be ok.
Posted on Jul 02, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Make sure the drainage port is closed as per the instructions. If you continue to have leakage you may have a leak in the tank.
Posted on Jun 15, 2007
Make sure the unit is level, this is very important. Check for blocked drain tube, which runs from the bottom of the drain pan under the cold coil to the outside. Clear tube with a piece of coathanger wire, be gentle.
Posted on Jul 15, 2007
Is it a split system? I had the same problem with my split system and and it was because the condenser line was mounted wrong. The line was mounted so the water had to go uphill and it was causing the condensation to leak through the front of the unit.
Posted on Aug 14, 2007
SOURCE: rv air conditioner leaking
In each of these cases I would check for proper connection of the return air vent to the A/C from below. Static pressure from insufficient return air could cause negative pressure to hold back on condensate drainage. when the unit is shut off the pressure becomes equal allowing water to drain. Also check air filter and clean if found necessary.
Posted on Jul 18, 2008
when the freon is released from the unit,you have to repair the leak,pull a vacumm to rid any moisture in system then refill with freon,if you dont have the equipment,it would be cheaper to just replace the unit
Posted on Nov 17, 2008
Tips for a great answer:
Aug 21, 2011 | DeLonghi PACA110 Portable Air Conditioner
Jul 11, 2011 | Fujitsu 24R1 Air Conditioner
Jul 04, 2011 | Friedrich Heating & Cooling
May 22, 2011 | Whirlpool Heating & Cooling
Dec 18, 2010 | Sanyo Split System Air Conditioner
Sep 06, 2010 | Emerson Quiet Kool 10NW16K Air Conditioner
Jan 10, 2010 | DeLonghi PAC C100 Air Conditioner
Nov 19, 2009 | Heating & Cooling
Jun 15, 2007 | Sharp CV-P09FX Air Conditioner
138 people viewed this question
Usually answered in minutes!