Question about True GDM-23FC-RF Refrigerator Commercial
Definitely a thermostat problem. Make sure that it is set on #3, make sure you have something in the box to provide a constant load (if you are worried about product freezing just put several gallons containers of water in there), set a thermometer on a shelf and let it run for several hours. Temperature should run 35-40f If it still freezes I recommend changing the thermostat. Not the easiest job on a True but the only real option. If it is too warm then raise the setting to #4 and run for several hours more and double check the temperature. It is normal for these box temperatures to "swing" quite a bit especially if empty. The thermostat actually senses coil temperature and not unit air temperature. Typically it cycles off when the coil reaches around 14f and then back on when the coil gets to around 38-40f.
Posted on Jul 07, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Mar 24, 2015 | True GDM-7 Beverage Cooler
Mar 22, 2015 | Beverage-Air MT27 Beverage Cooler...
Feb 01, 2013 | True TD-95-38-LT Beverage Cooler
May 11, 2011 | Beverage-Air EF48-1AS (46.6 cu. ft.)...
Jan 13, 2011 | True TDD-3-S Commercial Beverage Dispenser
Oct 24, 2010 | Whynter SNO ICE-100S 3 in 1 Portable Ice...
Jun 09, 2009 | Carrier Beverage-Air UR30GEFD Beverage...
May 20, 2009 | True GDM-7 Beverage Cooler
Jul 24, 2008 | True GDM-9 Beverage Cooler
186 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: