Question about Heating & Cooling
Wash out outside coil with hose with 30 degree downward starting at the top and work side to side to bottom and try again. If this don't help check evap coil (inside) for ice forming when unit is on. You should see a 15 - 25 degree drop from room temp coming out of discharge air. This will change with humidity indoors. as it drops temp will too.If outside coil is dirty or unit is low on gar it will cause high compressor and high disgharge lockout. Low gas can also cause freezing of indoor coil and loe temp or pressure lock out depending on type of protection incorporated.
Posted on Jun 30, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 01, 2013 | Bose Solo TV sound system - Black
Jun 03, 2008 | Whirlpool Kitchen Ranges
May 04, 2010 | Kenmore Elite 45986 Front Load Washer
Jan 19, 2010 | 1999 Pontiac Montana
Nov 14, 2009 | Garmin nuvi 205 GPS Receiver
Jan 02, 2009 | Maytag Neptune MAH5500B Front Load Washer
Dec 26, 2007 | Magellan MAESTRO 3100 98083401 GPS Device
Sep 12, 2007 | Sony SNT-V704 (SNTV704) Video Server
45 people viewed this question
Usually answered in minutes!