Question about Goodman GMS90703BXA Heater
Are you talking about the small 3 or 5 amp fuse in the furnace? If you are then the control voltage circuit to the condenser is shorted, Maybe dogs or rodents chewing it or the insulation is cut by a sharp piece of metal. Sometimes the contactor will go bad and cause the small fuse in furnace to blow. Look for the simple things first, like control wires shorted. Make sure the yellow wire from the thermostat goes to the outside unit and not to the common.
Posted on Jun 30, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 27, 2014 | Carrier Heating & Cooling
Aug 30, 2011 | Goodman CLQ36AR49 Air Conditioner
Aug 03, 2011 | Heating & Cooling
Dec 12, 2010 | Heating & Cooling
Dec 11, 2009 | Goodman Heating & Cooling
Nov 23, 2009 | Air Purifiers
Nov 12, 2009 | Goodman CLQ36AR49 Air Conditioner
Jun 24, 2009 | Goodman CLQ36AR49 Air Conditioner
May 13, 2009 | Goodman CLQ36AR49 Air Conditioner
May 05, 2009 | Heating & Cooling
499 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: