Question about Carrier 52PQ-515---3 Premier Series Heat Pump, 15000BTUH, 5.0KW, 230V PTAC Air Conditioner
yes you can buy the same rating fuse. and much better to put a circuit breaker, and more safe trip off.
how to check out your refrigeration compressor;
Modern Compressors have two operations that have to work together just to run. More items must be considered for them to work and work efficiently in systems. The 2 areas that must work together are electrical and mechanical. Either your compressor is broken inside or the motor and or start components are not working properly.
Ohm the compressor terminals to ground and across to each other.
1. If any read anything to ground the compressor is bad. If not go on to the next step.
2.Your readings between the compressor terminals should all be different and you should have 1 low 1 medium and 1 high resistance reading.
Add the low and mid reading together and the sum should be close to the highest reading. If it reads say 20% more or less then retest it a couple of times to confirm your not slipping on the terminals. If you get only 2 readings don’t panic wait 24 hours for the motor to cool off for sure and recheck it. If still no reading then your compressor motor is open. A new compressor or replacement of the appliance is required. If you now get the 3 readings described make a diagram you feel comfortable with as to where the wires go to each component before removing anything, then continue:
3 Assuming the above checks out: Get a new *Start relay *start capacitor if so equipped relay *external overload and *run capacitor if it has one. In other words everything that is external and attached to the wires or terminals on the compressor or wiring per your diagram and replace them on to the compressor. Then if it starts problem solved if it still does same thing the compressor is bad (broken mechanically inside the compressor) and you have to decide to replace compressor or replace the refrigerating compressor be it AC or Refrigeration.
*May or May NOT have this component:
MOST 99.999…% of refrigerators of the household type have a start relay of some kind and they vary in size shape and color. It plugs directly onto the compressor. SOME AC units but not all have one and it is different. These Resemble a box about 2”X2” X 3” with at least 3 terminals on it and these 3 terminals are marked 1, 2, & 5. Each of these will have at least 1 wire on them and there may be other terminals (4 & 6) as well that can be used with several wires on each.
* Start Capacitor
100% of AC and Commercial compressors that use a start relay (and remember some do not have one but those that do…) and only some domestic refrigerators use a Start Capacitor. At least 2 wires going to a black (usually) cylinder which is the start capacitor. Start Capacitors ALWAYS HAVE 2 or more Wires and ALWAYS HAVE TO HAVE A START RELAY.
MOST 99.9% of Household refrigerators, 80%+ of smaller commercial refrigerators, and most 90% of window unit AC’s but almost no central AC compressors Have an external overload. Those that do not have an internal overload. These vary in size and color and description a basic one is round 2 wires and generally black about quarter size USA AND IF USED ALWAYS MOUNTED ON THE COMPRESSOR with the other wires and terminals there.
Some domestic refrigerators (can be a small rectangular box) medium and larger refrigeration and (99.999%... of all) AC central and Window units have a compressor that requires a run capacitor. These type units also have a fan motor that can require a run capacitor. These Capacitors always have at least 2 wires and often 3 or more if the capacitor also is wired to the fan motor.
If a compressor is tight due to linear expansion from heat a tip worth remembering is as something cools it contracts, except for water at freezing. A few times I have gotten a compressor to start after leaving it off for 6 to 12 hours then retrying it. See the compressor unless left off for 6 to 12 hours and sometimes as long as 24 hours may have expanded parts from heat. About 1/2 the time it is ok after new start components are installed with a start capacitor and relay. The other 1/2 the compressor will be ok for a day or 2 then stop again. A “hard spot” in the movement of the internal parts in the compressor, and stopping on this hard spot it can’t overcome the “tightness”.
If you follow most of these steps above you will arrive at a correct diagnosis well over 90% of the time ( allowing for what is unusual or for misunderstandings)
10 years of doing refrigeration and this has not changed..
Please rate me as high as you can and ask me to clarify anything you don’t understand.
Posted on Jun 30, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Mar 10, 2015 | Carrier 52CQ-312-4 Comfort Series Heat...
Jan 26, 2014 | Heating & Cooling
Jul 23, 2012 | 2006 Honda Jazz 1.5
Aug 01, 2011 | Carrier XQB183D Air Conditioner
Jan 24, 2010 | Honeywell ER150B Air Conditioner
Oct 27, 2009 | Heating & Cooling
Jul 05, 2009 | Carrier 38BRC036 Air Conditioner
Jun 09, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Feb 07, 2009 | Dometic Rooftop RV Air Conditioner
103 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: