Question about Carrier 38CKC060 Air Conditioner
My carrier comfort zone 2 thermostat keeps flashing E2 and is not cooling my house properly. Does anyone have any idea what this warning light means and how I can fix this issue?
My Carrier guy said that E2 means a low voltage problem. He also said that E1 means a high voltage problem, but also threw in the comment that without high voltage there would be no low voltage either, so it could read E2. In my case, the evaporator is up in the attic and there is a float shutoff switch that shuts the unit off when the drain is stopped up and water backs up into the pan--so that the water doesn't run down onto the sheetrock on the ceiling. So the shutoff switch cuts off the low voltage and E2 shows on the thermostat. Clean out the drain and the water doesn't back up into the pan any longer.
Posted on Jun 18, 2013
E-2 was flashing on my Carrier thermostat and sometimes it maybe caused by a boken return temperature sensor but this time it was a burned out pump motor on the side of my unit downstairs that pumps out the condensation. Good Luck.
Posted on Jul 31, 2012
Due to thermister fault this problem occurs. if not go for pcb replacement.
Posted on Feb 04, 2015
Our zone 2 heater was not turning on, and E2 was flashing on the thermostat. We solved the problem by changing the batteries in the thermostat.
Posted on Feb 04, 2015
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 14, 2015 | Carrier Heating & Cooling
Aug 27, 2011 | Carrier Heating & Cooling
Sep 25, 2010 | Heating & Cooling
Oct 12, 2009 | Carrier 38CKC042 Air Conditioner
Jul 01, 2009 | Carrier 38CKC042 Air Conditioner
Jun 24, 2009 | Carrier 38CKC060 Air Conditioner
Feb 18, 2009 | Carrier 38CKC060 Air Conditioner
Jan 19, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Dec 03, 2008 | Carrier Heating & Cooling
Sep 04, 2008 | Carrier Heating & Cooling
5,629 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: