Question about General Electric G.E. - INDUSTRIAL SYSTEMS TPL412R 125 AMP OUTDOOR MAIN LUG LOAD CENTER
Just installed 125 outdoor GE TPL412 RP subpanel. Hooked up the 4 wire 240 line from the main panel - ground to one of the two small bars used for circuit grounds and neutrals. Hooked the white neutral to the first large lug, the red wire to the second lug and black wire to the third large lug in the box. Both circuits in the first space are hot, neither circuit in the second space is hot, both circuits in the third space are hot but neither circuit in the forth space is hot. What am I doing wrong?
This is not 3 phase power...you have two legs of 120 ...the red wire? This leg is not a voltage source therefore that wire is not going to fire up that lug ...you only need 3 wires to make this circuit and a neutral is a redundant leg for this box
Posted on Jun 29, 2009
White t o NEUTRAL BAR
green to GROUND BAR
black to A PHASE (BUSS BAR)
red to B PHASE (BUSS BAR)
4 WIRES FROM MAIN PNL
NEUTRAL BAR MUST BE ISOLATED, DO NOT BOND TO
white wires to NEUTRAL BAR ONLY
BKR A PHASE BKR
3 B PHASE 4
5 A PHASE 6
REPEATS TO BOTTOM OF PNL.
GREEN wires TO GROUND BAR only
Dont forget GROUND ROD,STEEL BOND,METAL PIPE BOND. PROPER GROUNDING = NO 911 CALLS
Posted on Jan 14, 2015
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 04, 2012 | Bryant Westinghouse Bqc Quad Circuit...
Oct 20, 2012 | Square D Qo 125 Amp 24 Circuit Indoor...
Aug 15, 2012 | Your One Source Homeline Load Center, 200...
Mar 02, 2011 | General Electric GE INDUSTRIAL SYSTEMS...
Jan 20, 2011 | General Electric GE 56941 24-Hour Outdoor...
Oct 03, 2010 | Siemens 100 Amp Main Breaker Renovation...
Dec 31, 2008 | Your One Source Homeline Load Center, 200...
Nov 30, 2008 | Dayton Electric Heater
Nov 22, 2008 | Fahrenheat Electric Convector Baseboard...
503 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: